Heating And Air Conditioning Sachse TX
When you need expert comfort solutions in Sachse, TX, whether it's HVAC repairs, indoor air quality services and more, AC Pros is the company for you! We're known for our commitment to professionalism and customer satisfaction.
Read our reviews to see why homeowners in Sachse, TX are continuously happy with our team's skilled work.
for Sachse, TX
Our Reviews by City
Gilbert - Sachse, TX 75048
Excellent Service !!
Anne - Sachse, TX 75048
Very Informative !!
AC Pro service call
Tony - Sachse, TX 75048
AC pro technician Samual Hamons is very professional, thorough, and a kind person. He set about his tasks and resolved our ticket in a flash. Before leaving our home, set down with we to review what was discovered during the service event. He brings a 4 start rating.
Joel's great. Courteous and efficient. Thanks.
Alan - Sachse, TX 75048
He's definitely an expert!
Steve - Sachse, TX 75048
Bob at AC Pros is truly outstanding, he is super trustworthy, he's respectful to us and our house, he really knows HVAC better than anyone, he's thorough and speaks "plain English" when describing the work completed (English as opposed to tech-speak that you need a degree to understand). I highly recommend this AC Pto (Bob) and the company.
Scott - Sachse, TX 75048
AC unit was not working, company able to schedule an appointment same day. Technician arrived on schedule. Technician personable and knowledgeable, resolve the issue quickly.
Tom - Sachse, TX 75048
Francisco did a outstanding good.Great tech.Thank you
Mike - Sachse, TX 75048
Joel - Great Serviceman
Anne - Sachse, TX 75048
Told us our new unit you installed is still running fine !! Joel was pleasant and informative !!
Jason was superb. Explained everything in detail.
Alan - Sachse, TX 75048
No heat. Upon arrival the furnace was opened and the board was displaying a code for an open flame rollout circuit. The upper flame rollout switch was reset. The burners, other safeties, vent system, and heat exchangers were all checked. The system was then ran for an extended period of time in order to ensure the switch did not trip again. The system is heating properly at this time.
Preformed the fall maintenance, found the unit to not be in the greatest of shape but operational. No gas leaks or carbon monoxide detected. System is in dire need of a cleaning and due to the age suggest the customer gears up for replacement.
Preformed the 2 system fall maintenance. Found the upstairs system to be working properly. Both filters are dirty and need to be replaced. Found the downstairs furnace to be 24 years old. The system is operational at this time and 5he customer wants to see how long it will last since they just purchased the upstairs unit.
Preformed the fall maintenance. Found the heat exchanger to have multiple cracks in it. Turned Gas off to the system. Left pricing for the customer.
Fall heater tune up one system. Upon arrival the thermostat had been disconnected from the internet and mobile device. The thermostat was reset and reconnected to the internet as well as the homeowners phone. The system was then turned on in heat mode and tested. The blower motor, heat exchanger, burners, flame sensor, furnace safeties, vent system, gas lines, hot surface igniter, and electrical connections were all inspected. The filter was changed with one provided by the homeowner. The system is heating properly at this time.
One of the teardrop limit switches from the flue pipe head trip due to wind conditions previously. Reset and system came back on. No charge since maintenance was done October 13.
Performed one system gas maintenace on 2015 American standard gold series furnace. 80% furnace with ECM motor. Cleaned flame sensor. Proper amp draws on inducer motor And blower motor. No issues with sequence of operation. customer replaces his air filter on schedule.
Customer stated that the AC was not keeping up during the heat I found where water may have been in the drain pan I believe that the unit may have been backing up and shutting off will return on Monday to inspect AC when temperature is above 60° inspected furnace tested amp draws cleaned burner assembly and flame sensor everything is working properly at this time
Found thermostat not working replaced system is working at this time
Heat performance tuneup times two systems. Inspect blowers, evaporators of ductwork. Test all safety features high limits and rollouts. No carbon monoxide or gas leaks detected in the home. Advised Everett about some bracing that needs to be maintained in his attic. Systems are heating properly at this time. Changed out filters client supplied.
preformed after install inspection
Zac Preformed post install inspection.
Dispatched for a no cool single system home. Upon arrival spoke with homeowner and found out issues. She has been having in the past. Checked outdoor unit. System was extremely low on R 22. Sent the estimate to Claudia for the repairs. She has chosen to only do the refrigerant today. System is 20 years old. I am leaving a quote for a 15 seer, York, and Trane
Found a leak in the evaporator coil. See pictures. Customer reason a parts and labor warranty with another company. They will try and resolve the issue with them.
On arrival found the txv to be clogged and the high pressure switch to not be engaging properly. Recommend replacement at this time. Customers opted for the 18 seer 2 stage system. Replacement is for tommorow on the upstairs system. See pictures.
Zac Preformed maintenance with all proper checks and cleanings. found both capacitors to be bad and recommended new thermostats and manual dampers
Came by today to verify that unit is working properly. And also to re-do the financing.
Found bad thermostat will need to come back out and replace 825 under warranty communicating thermostat
replacing 2 8inch returns. 1 in each bedroom per joel
Dispatched for a no cool single system home. Upon arrival system was running. I reworked the drain line so that the primary drain line was not flowing up hill. Client stated that it was struggling during the daytime. I found drainage issues in the Attic that I corrected. Went to the outdoor unit and found it severely impacted with dust dirt and debris. Thoroughly clean the condenser. Gauged up and found that the system is low on refrigerant. Performed a leak search and found a leak on the evaporator coil. It is a very slow leak. Client would like to talk to her husband about the labor cost which is $2,500. The disconnect was faulty and I showed client. Changed out pull spaid to a true disconnect. Client will let us know if they want to change out the compressor later
Found capacitor dead as well as the system low on refrigerant and compressor pulling 90 amps on Startup recommend repairs or potentially system replacement due to the high cost of repairs
Customer wants to get a second opinion and chose to do nothing today
AC performance tune up times three systems. Filters have been changed recently. Client stated that the middle thermostat has not been cooling properly. System only has a 2° split. We are looking for a 16 to a 20. I checked nordon warranty and verify that it is out of warranty. It only carried a 5-year warranty. I am leaving quotes for a new 2-ton complete. The estimate is for a 15 seer, 16 seer, and 18 seer. If we added refrigerant it would only leak out before winter time hits. These are heat pumps so they are used year round.