Heating & AC Repair, HVAC Contractor Near Richardson TX
Expert Cooling & Heating Company Near Richardson, TX
In the 25 years we have been in business, AC Pros has strived to serve Richardson with impeccable service on all things HVAC. Our clients make our business, which is why we devote so much time and energy to things other companies might not consider as important. Some of the things which make us go above and beyond with air conditioning and heating service include:
- Our technicians are factory trained on the latest technology so that they can service your unit the right way on the first call.
- We offer a one year maintenance contract with every new HVAC installation, guaranteeing any kinks will be worked out on our watch.
- We provide 24 hour, seven days a week emergency service with no overtime fees.
- Our team is devoted to technical excellence and safety. Technicians at AC Pros have undergone the latest HVAC education and safety training.
- We are a Trane Comfort Specialist Dealer, offering installation and repair services on this exclusive and premier brand.
As a family owned and operated business, our goal is to be there to serve you. We offer the following services and more in the Richardson area:
- Air Conditioning Maintenance, Repair & Installation
- Heating Maintenance, Repair & Installation
- Air Condenser Cleaning & Repair
- Indoor Air Quality Control
- Blown-In Insulation
- Window Installation & Replacement
- Duct Cleaning
We have included our reviews below and invite you to read them. They showcase our technical expertise and commitment to our customers. For more information on AC Pros, or to schedule an appointment, call us today at (972) 591-0199.
for Richardson, TX
Our Reviews by City
Paul - Richardson, TX 75081
My wife had concerns about our HVAC system. Sam addressed all of her concerns openly and honestly, made some minor adjustments to the system and recommended more insulation in our attic.
Competent, honest, friendly service.
Eric - Richardson, TX 75081
AC pros has maintained my AC/heating system for years and always performed well. Joel did a great job cleaning up the blower fan and checking my system. He has been out here before in years past and continues to provide great friendly service.
Rauber - Richardson, TX 75080
Great job from start to finish. Service began when AC Pros owner showed up at my home with two electric heaters for my safety and comfort. Our gas company had shut off the gas to my home due to several discovered and unknown gas leaks and I was without heat or hot water during the Christmas holidays and after. We explored the option of converting to an all electtric home and purchased a new HVAC'/heat pump from ACPros . The scheduling, coordination with my electrician and plumber. instalation of new units, and followup with testing , pipe adjustments and instructions were flawless. My heartfelt thanks to all the staff involved in this job.
Farren - Richardson, TX 75080
Didn't cut corners
Ted - Richardson, TX 75080
Justin did what it took to do the job right. He discovered he needed tools (concrete bits) needed to attach conduit to outside of the house so he took the time to purchase what he needed to complete the task. Only shortcoming was he was unable to repair can light that was stepped on during ac installation.
Adam - Richardson, TX 75080
Jason was friendly, knowledgable, and helpful.
Good & courteous technician
Scott - Richardson, TX 75080
Ahead of the my schedule time, Sam called and asked if it was ok to come earlier. When he showed up he was very polite. He inspected my heating unit. He diagnosed the issue. We discussed the solution all within reason. Sam is five stars in my book. Thank You.
Satisfied with the thoroughness of the service
Robert - Richardson, TX 75080
Carol - Richardson, TX 75082
Michael - Richardson, TX 75080
Winter Heating Check
James - Richardson, TX 75082
Kevin - Richardson, TX 75081
Gina - Richardson, TX 75081
A C Pros has been great. Joel explained evert thing and was very nice to have inspect my heating system
Bill - Richardson, TX 75082
Fall '22 system check-up
Rick - Richardson, TX 75081
A C Pros has been great
Bill - Richardson, TX 75082
Tech was only here for 20 to 25 minutes and half of that was discussing my cold spots in my house. Not sure how well he checked out my heating unit in the 10 minutes he was in the attic. Usually, tech takes longer than that when maintaining my unit. Don't think I got my money's worth on this visit.
Justin Sullivan checkup on gas furnance
Dennis - Richardson, TX 75081
Great service . Very knowleable
AC Pros goes the extra mile!
AP Enterprises - Richardson, TX 75081
AC Pros did a great job helping me with both a cooling problem and heat check! Fast, efficient, very nice and knowledgeable Associate for a great price. Way to go AC Pros!
Timely and Professional!
Andy - Richardson, TX 75082
Joel was able to come in, do his evaluation and get the heat going in the house is a very timely manner! Super nice and was understanding of the current needs and made recommendations for the future. It was good to meet Russ too! Thank you gentlemen!
Joel has ALWAYS been very thorough and very knowledgeable about the work he seem to love. We love everything about him. U
Wesley - Richardson, TX 75082
Joel is the best tech we have had come to our home from any company. He is like family to us and we are so lucky to have him come to our home.
Just was so professional and knowlegeable. AC Pros has a great team of technicians !
Daniel - Richardson, TX 75081
Dale - Richardson, TX 75082
Jason was polite and explained exactly what he was doing plus very informative as to how I could extend the life and production of my unit.
Justin - Richardson, TX 75081
Justin was extremely helpful and knowledgeable and went above and beyond to make sure the problem was resolved.
Excellent service and great technician
Richard - Richardson, TX 75081
James - Richardson, TX 75080
Upon arrival checked in with the customer the following are my findings customer indicated to me that she's having problems with the temperature rising as well as one of the rooms not getting the correct amount of air flow investigated further determined that there was a significant amount of insulation and the thermostat having settings that were not conducive to thermal optimals Remediated and system is working properly at this time
Arrived and checked unit for leaks and places where outside could be coming in. Attic crawl space was looked at and video will be attached. Found an odd jumper duct half wrapped with open end making it a perfect place for rodents, one of which was found dead right above customer units. Given lack of insulation there's no way to eliminate all outside air from being pulled in. Attic access bis next to the chimney suite and lack ofbsealnarounf thencutout will result in smoke smell.
The following are my findings for today's visit Customer indicated to me that the unit had a funny smell on startup as well as him having a hot and a cold spot in two of the rooms Explain to the customer about dirty socks syndrome as well as remediated the air system is working perfectly it is going on a year and a 1/2 old now only recommendation is continual maintenance
Heat performance tuneup times one system. Client changes his filter. Inspect blower, evaporator and ductwork. Test 10K W heat strips. Pull blower wheel and cleaned squirrel cage and blower wheel to. Added 1 pound of R410 a. Condenser heat pump is 21 years old. Client would like to get as much life is you can out of it.
Completed install on recently installed equipment. Power was on so I programmed the 824 thermostat and the Tam nine air handler. Need to return another day in order to correct drains so that the filter can be changed out on future visits. Office will call and schedule date to return.
Heat performance tuneup x1 system. Inspect and test blower motor. Cycle heating test all safety features, high limit switches and rollouts. No carbon monoxide or gas leaks detected. Clean flame sensors and inducer port. Tighten all wire connections. System is operating fine. Leaving quote for plumbing work to restructure existing COPPER drain.
Found a roof leak in attic . Showed customer where it was and they will call a roofer .
2 system checkup on trane gas units we installed. Form completed and attached with issues and recommendations found. Customers thermostat was setup and connected to nexia. Will leave quotes for thermostat upgrade and room sensor.
Heat checkup on 2 pancake units. Form completed. No issues found at this time.
Form completed with recommendations and issues found. Can confirm heat is running st this time. Listed are register sizes for house. Dynamicaqs.com for information on the IAQ
HVAC Service - Upon arrival checked in with customer the following are my findings Found The unit working properly at this time my only recommendation is continual maintenance found 0 parts per million for carbon dioxide and no natural gas leaking at this time customer
HVAC Service - Upon arrival checked in with customer the following are my findings Found the unit working properly at this time
HVAC and Ductwork Service - Upon arrival checked in with customer the following are my findings Found the unit working properly at this time Only recommendations is continual maintenance please see pictures attached and estimate Found 0 parts per million for carbon dioxide and no natural gas leaking at this time Found what appears to be Lint inside the attic and formed the customer he is going to investigate further
AC Repair & Thermostat Issue - Dispatched for a no cool on the north east corner of the building. Arrive to find heater was running. Thermostat was off. Went to the rooftop and traced out problem with the thermostat wire. It was making contact for the heating circuit due to UV rays, deteriorating the insulation on the wire. made necessary repairs. System is operating properly at this time. No charge today since the maintenance was done last week.
HVAC Service - Upon arrival checked in with customer the following are my findings Found the unit working however the draft motor is over amping and needs to be replaced please see pictures attached and estimate also found 0 parts per million for carbon dioxide and no natural gas leaking at this time however
Heating Service - Upon arrival checked in with customer the following are my findings found the unit working properly at this time only recommendation is continual maintenance and informed the customer about buying Honeywell filters in the future he understands and will do so moving forward found 0 parts per million for carbon dioxide and no natural gas leaking at this time
Heating & AC Repair - Arrived to find fan wire was not connected.. It was put back system cycled and is cooling at this time. The customer was made aware both his systems drain uphill and will not drain correctly until they're fixed.
HVAC Repair - Put thermostat wire through conduit and anchored into mortar to secure then re wired in the condenser. Fixed all the wires in attic that were spread out using zip ties and getting rid of the wires that were from old unit . Also gave a quote for duct cleaning that he will want when construction is done soon. 1,093
Apon arrival checked in with customer the following are my findings Customer indicated To me that there was a sound coming from the downstairs unit that is continuously reaccurring unable to locate source of sound will have to investigate further into the future Other than that the system is working properly at this time only recommendation is continual maintenance please see pictures attached Found 0 parts per million for carbon dioxide and no natural gas leaking at this time
Board is bad and its discontinued. System is a 1993 . Wants quote for replacement.
Miscommunication happened we will be back out in the summer to perform the work Customer understands and is copicetic
Heat performance tuneup on rooftop units. Inspect blowers, evaporators and belts. test all safety features high limits and and roll outs. Tightened all wire connections. Changed out all filters. All units have good temperature rise. No carbon monoxide or gas leaks detected. There are still three units that are disabled on the AC side. Clean flame sensors and inducer ports. No belts were changed out on this maintenance. Systems are heating properly at this time.
Form completed and no issues found. Can confirm heat is running at this time. Airflow changes were made so please call Jason with any issues.
Form completed with pictures and recommendations. Can confirm heat is running at this time.
Heat Service - Checked system in heating and cool verifying a 20 degree split . Checked condensation lines and duct work. Had to add 3 lb 410 a since it was to cold to add freon when installed . System had an alarm for low pressure switch due to low 410 a. System in now charged .