Heating And Air Conditioning Richardson TX
Expert Cooling & Heating Service | Richardson, TX
In the 25 years we have been in business, AC Pros has strived to serve Richardson with impeccable service on all things HVAC. Our clients make our business, which is why we devote so much time and energy to things other companies might not consider as important. Some of the things which make us go above and beyond with air conditioning and heating service include:
- Our technicians are factory trained on the latest technology so that they can service your unit the right way on the first call.
- We offer a one year maintenance contract with every new HVAC installation, guaranteeing any kinks will be worked out on our watch.
- We provide 24 hour, seven days a week emergency service with no overtime fees.
- Our team is devoted to technical excellence and safety. Technicians at AC Pros have undergone the latest HVAC education and safety training.
- We are a Trane Comfort Specialist Dealer, offering installation and repair services on this exclusive and premier brand.
As a family owned and operated business, our goal is to be there to serve you. We offer the following services and more in the Richardson area:
- Air Conditioning Maintenance, Repair & Installation
- Heating Maintenance, Repair & Installation
- Air Condenser Cleaning & Repair
- Indoor Air Quality Control
- Blown-In Insulation
- Window Installation & Replacement
- Duct Cleaning
We have included our reviews below and invite you to read them. They showcase our technical expertise and commitment to our customers. For more information on AC Pros, or to schedule an appointment, call us today at (972) 591-0199.
for Richardson, TX
Our Reviews by City
Very proffesional service Tech
Roy - Richardson, TX
On time as scheduled. Very efficient.
Joe was very professional
Paul - Richardson, TX
Joe was very professional. He explained clearly what he was doing, thoroughly checked everything, and was polite.
Tom - Richardson, TX
Once again, Joel Sisk does a great job taking care of our HVAC system.
Chris - Richardson, TX
Francisco called ahead of time to let me know he was on his way. Showed up very professional w/ slip on shoe protectors inside. Performed the maintenance and went over the report with me. Very good service.
maryanne - Richardson, TX
Jim at AC pros gets me connected to the best technicians. Jeff was prompt and courteous with his arrival, and kept me informed about what was going on, and made sure I knew what we were accomplishing that day.
Tom - Richardson, TX
Cheri - Richardson, TX
Jeff was great. He listened to my explanation of what was going on, then checked things out himself. He came back and told me what was going on and the remedy and the cost. I proceeded to have him remedy the situation. He spent time with me going over various poosiblities all whale waiting to make sure my humity level was get back in balance. Very nice, knowledgeable and efficient.
Larry - Richardson, TX
The AC Pros tech, Jeff Stevens, went above and beyond....he not only troubleshot my AC issue, but he solved investigating a plumbing issue i had under my crawl space! Nice job, Jeff !!
Steve - Richardson, TX
Jeff did a great job.
Rick - Richardson, TX
Marty - Richardson, TX
Farren - Richardson, TX
Joel always does a GREAT job!
Michele - Richardson, TX
We always call AC Pros if we have a problem with our air conditioner. They respond quickly are always very professional. I know that they are not going to try to sell me something I do not need and will repair it right the first time.
James - Richardson, TX
Joel does an outstanding job. He is friendly and knows his stuff and lets me know what is going on with the units.
Great service and kind worker!
Chance - Richardson, TX
Thank you to Mr. Sanchez who came and checked out our AC. He was very knowledgeable and helped get us checked out quickly. Thank you for keeping us cool in this summer heat!
Rapidly found the problem
Rayburn - Richardson, TX
Roger - Richardson, TX
Francisco did a great job in his review of the installation.
punctual, courteous, most professional. feel secure that review of heating and airconditioning units done properly.
BT - Richardson, TX
On time, knowledgeable, efficient
Jerry - Richardson, TX
Thorough and Efficient
Mary - Richardson, TX
Francisco was polite, efficient, thorough and problem solving.
Super fast and great customer service
Adam - Richardson, TX
Greg - Richardson, TX
Wesley - Richardson, TX
Great Service, awesome price!
Connie - Richardson, TX
The technician was knowledgeable, respectful and efficient.
Robert - Richardson, TX
AC performance tuneup times one system. Change out filter client supplied. Verified primary drain is clear and treated with drain solutions. Check thermostat for proper operations. Indoor evaporator coil has a small leak. I added 3 pounds are 410 A to achieve a 10Â° sub cool. Office will call and schedule date to return to change out coil under train 10 your part warranty and five year labor warranty
Perform 1 system maintenance checked pressures split tested capacito washed condenser coil changed customer supplied filter system cooling properly at this moment C/u m; 4TTR6036J1000AA S;19064JW85F Evap coil; m:4TXCB004DS3HCAA S:19302w075G
Perform 1 system maintenance checked pressures split tested capacitor, washed condenser coil put noise isolator to stabilize pad it was wobbling specs are on maintenance form system is cooling properly at this moment
Perform 2 system maintenance checked pressures split washed both condenser coils also changed customer supplied filters specs are on maintenance form both systems cooling properly
AC performance tuneup times one system. Treat drain lines with drain solution. Inspect blower, evaporator and ductwork. Remi halo bulb is defective. We just installed last year. Office is ordering a new one and will call and schedule date to return to install. Check outdoor unit. Change out filter client supplied. Refrigerant level good at this time. Wash condenser coil. System operating at manufacture specs at this time.
AC performance tuneup times one system. Change out filter client supplied. Inspect blower, evaporator. Checked thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacture specs at this time.
Primary drain was clogged up, cleared drains.
Completed diagnosis, indoor/outdoor units does not have sufficient voltage. Home owner needs an electrician. Also replaced 20x25x4 Honeywell media filter.
Perform 1 system maintenance checked pressures and split r22 system recommend replacing the filter washed condenser coil specs are on maintenance form systme cooling properly at this moment
Customer wanted to upgrade thermostat, installed T6. Honeywell thermostat. Jim the comfort advisor is scheduling some work to be done.
Perform 2 systme maintenance checked pressures and split washed cinder coil tighten electrical connections specs are on maintenance form both systems are showing age but cooling properly at this moment
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Verified primary drains are clear at this time. Treated both drain lines. Checked thermostats for proper operations. Check out door units. Refrigerant levels good on both systems.Cast capacitors and contactors. Systems are cooling properly at this time.
Completed diagnosis, humidity in house was 80%up on arrival and sub cooling was at 1.5, below specification. Charged system with 3 pounds of 410a, humidity now is at55%.
Cancelled this invoice and I will re book.
Arrived to bad capacitor replaced with turbo systme cooling properly
Humidity underneath the house, at first glance could not see any water leaking. When in a far as I could go and water was leaking from a busted pipe. Customer will call plumbers back out.
Customer cancelled at the door.
Arrived to system low on refrigerant added 3 lb of 410 recommend a leak search no guarantee on refrigerant will talk to office to schedule leak search systme cooling at this moment
Condenser was not coming on, replaced sealed contactors and added 1pound of 410a.
Smaller unit was coming on, replaced with 35/5 Turbo run capacitor. Everything is cooling properly.
Arrived to clogged drain blew it out and treated system draining properly at this moment
Condenser fan motor was running constantly. Arrive to find Francisco had wired it incorrectly. Made necessary adjustments to wiring and system is operating properly at this time.
Install new 930 Sensor
One unit, compressor was not coming on, replaced Turbo run capacitor, everything is working ok.
Pulled cover over attic access.