Heating And Air Conditioning Richardson TX
Expert Cooling & Heating Service | Richardson, TX
In the 25 years we have been in business, AC Pros has strived to serve Richardson with impeccable service on all things HVAC. Our clients make our business, which is why we devote so much time and energy to things other companies might not consider as important. Some of the things which make us go above and beyond with air conditioning and heating service include:
- Our technicians are factory trained on the latest technology so that they can service your unit the right way on the first call.
- We offer a one year maintenance contract with every new HVAC installation, guaranteeing any kinks will be worked out on our watch.
- We provide 24 hour, seven days a week emergency service with no overtime fees.
- Our team is devoted to technical excellence and safety. Technicians at AC Pros have undergone the latest HVAC education and safety training.
- We are a Trane Comfort Specialist Dealer, offering installation and repair services on this exclusive and premier brand.
As a family owned and operated business, our goal is to be there to serve you. We offer the following services and more in the Richardson area:
- Air Conditioning Maintenance, Repair & Installation
- Heating Maintenance, Repair & Installation
- Air Condenser Cleaning & Repair
- Indoor Air Quality Control
- Blown-In Insulation
- Window Installation & Replacement
- Duct Cleaning
We have included our reviews below and invite you to read them. They showcase our technical expertise and commitment to our customers. For more information on AC Pros, or to schedule an appointment, call us today at (972) 591-0199.
for Richardson, TX
Our Reviews by City
As always, Joel did a great job!!!
Sandy - Richardson, TX
This company is easy to work with and very friendly. I would recommend them.
Lenore - Richardson, TX
Very friendly and courteous service and informative
Professional and efficient
David - Richardson, TX
Jeff was prompt in calling and coming. No wasted time or effort. Curious to check on all performance items and then report all findings. A routine seasonal maintenance check performed well. He paused to take performance and air filter questions. Very knowledgeable. Trusted too Nicely done. Thank you
Elliot - Richardson, TX
Jim - Richardson, TX
Jeff quickly solved my problem
Rodolfo - Richardson, TX
On time and efficient
Fast and informative
Dennis - Richardson, TX
He showed up on time and got my air running again quickly, I asked him other info about my vents and other things and he answered all my questions. I will definitely be using them again 😁
BT - Richardson, TX
Great job. Feel safe.
Steve - Richardson, TX
Francisco went above and beyond to make sure we got the correct part to fix our AC.
Very good service
Randy - Richardson, TX
Fransisco was great. He found the problem quickly and explained it in a very accessible way. An overall great experience.
Francisco is courteous, a competent technician, a great communicator and extremely patient person.
Tammy - Richardson, TX
Michelle - Richardson, TX
Eliot - Richardson, TX
Joel knows his stuff. Quickly saw that the problem was the compressor start capacitor was bad. I think the part cost was expensive but the system was up and running in less than 30 minutes.
Steve - Richardson, TX
Paul - Richardson, TX
Joel seems to know what he’s doing, and he very polite and informative.
Eddy - Richardson, TX
Determined problem and fixed it promptly
Great service, quick fix!
Doug - Richardson, TX
As always, AC Pro’s completes the visit with great service and a quick fix!
Brett - Richardson, TX
The service tech came out and was very upfront about what I could expect to pay. He gave me some advice to minimize the same problem in the future.
Katie - Richardson, TX
It was great
super technical !!
Larry - Richardson, TX
Feel that my system is secure
Claudia - Richardson, TX
Love this company. Have used them for 19 years-always professional and friendly. They always make me feel secure in that my system is working properly and they will be there when I need them. Love the automatic calls from a live person to schedule my service checkups. Francisco provided the service today and was great! Won't use any other company for my air and heating needs.
Very nice young man
Russell - Richardson, TX
Francisco was very nice and polite. I felt safe having him in my house.
Jeff is so Professional !
Daniel - Richardson, TX
Jeff is excellent !
So thankful for Joel’s work!
Jim - Richardson, TX
Joel was able to come on Sunday afternoon and quickly diagnosed our a/c problem. He was able to quickly replace the faulty part.
Gina - Richardson, TX
Upstairs primary drain line was clogged up tripping float safety switch, not allowing equipment to energize. Cleared out drain line, everything is working properly.
Perform 1 system maintenance checked safety components co levels at arrival indoor blower motor was bad warrantied out. System needs more return a 16 inch or 2-8inch returns system is heating properly at this moment
Heating performance tuneup times two systems. Changed out filters client supplied inspect blower, evaporator and ductwork. Test all safety features high limits and roll outs.Test amp draw on electric strips. 21.2 A on each one. Check thermostats for proper operations. Checked refrigerant level on upstairs unit. Washed condenser coil. Addressed rattle on the upstairs air handler. The blower diverter was loose causing it to rattle at certain times. System is operating at manufacture specs at this time.
Arrived to find main breaker left off turn on system came on
Perform 1 system heat maintenance checked safety components checked heat exchanger and co levels cleaned flame sensor system is heating properly at this moment recommended duct cleaning due to old ductwork
Heating performance tuneup times one system. Advised client that the filter needs to be changed within the next two weeks. Check all safety features high limits and roll outs. Engaged test mode on the IFC three times. Tested temperature rise 42Â°. Check blower, evaporator and ductwork. No Carbon monoxide or gas leaks detected in home. Remounted thermostat with a blank off plate behind it. System operating at manufacture specs at this time.
Performed maintenance check on heater, everything checked out no problems found at this time.
Completed heat check, found bare places so attic insulation needs to added, to control temperature. Also not enough ventilation on roof. Flame patterns, igniter and flame sensor are in good shape. No gas or carbon monoxide leaks and temperature rise and gas pressure is good. Changed out media filter. Homeowner purchased a Gold membership.
Primary drain was clogged up on the drain line causing the system to shut off. I had to re-pipe 4 feet of the PVC because the copper was no good. System draining properly and operating properly at this time
Removed extremely dirty filters clean grills and added 1 lb of 410 system cooling properly at this moment
Heat maintenance check: flame is sensing low micro amps, needs to be replaced. Also recommended adding Reme halo, declined repairs right now. Attic insulation is ok, return filter is dirty homeowner will replace it. Carrier furnace M#310AAVO36070AAJA. S#3804A27330. price on Reme halo$995.00.
Arrived to find system frozen will let it drout out and come back to diagnosed
Heating performance tuneup times one system. Changed out filter client supplied. Inspect blower, evaporator and ductwork. Tested all safety features higher limits and roll outs. Clean flame sensor, Induce her port and ribbon burners. Check thermostat for proper operations. No carbon monoxide or gas leaks detected. Hit exchanger still look like new no cracks. System operating at manufacture specs at this time.
System was drout out found system low on refrigerant r22 found leak in evaporator coil system is fan coil had Russ come out and give options
Arrived to find system frozen turn system off we have to let system drout out and come back tomorrow
Heat maintenance one system, cecked for gas and carbon monoxide leaks gas pressure, temperature rise and inducer draft motor was functioning properly. Recommended surge protectors.
Completed diagnosis, no problems found at this time, flame sensor micro amps were at 2.5 Which was good.
Perform 2 system heating maintenance on recently installed systems tighten connections changed customer supplied filter tested safety components and co levels found no issues system is heating properly at this moment recommended rheme halo and attic Insulation top off
Perform 1 system heat maintenance checked safety components changed customer supplied filter checked co levels recommend attic insulation system is heating properly at this moment
Completed heat maintenance, flame pattern/flame sensor/inducer draft motor and temperature rise and return filter was good. No problems at this time.
Completed diagnosis no heat, burners were not coming on. Lit pilot. Furnace is about 30 years old, heat exchanger is worn out. Furnace needs to be replaced.
Arrive to find indoor blower motor bad furnace is from 1992 will have Russ come out and give options tomorrow no charge since we were just out yesterday
Condensate pump was clogged up. Remove pump and brought it outside and cleaned all the soupy moss off of it. Poured water down pump to verify that it was going to work. System is draining properly at this time. Recommend a maintenance program because the heater is very old And the heat exchangers are probably defective.
Found condenser not running. 40+5 run capacitor was dead. Removed and replaced with turbo 200 X. Park carries a five year warranty. System is cooling properly at this time.
No cool on the rooftop unit closer to the front of the building. I determined that L 2 only has 33 V. And electrical contractor will be needed to remedy the problem