Heating And Air Conditioning Roanoke TX
When you need expert comfort solutions in Roanoke, TX whether it's HVAC repairs, indoor air quality services and more, AC Pros is the company for you! We're known for our commitment to professionalism and customer satisfaction.
Read our reviews to see why homeowners in Roanoke, TX are continuously happy with our team's skilled work.
for Roanoke, TX
Our Reviews by City
James - Roanoke, TX 76262
As always, great service
James - Roanoke, TX 76262
I've used ac pros for many years and have gotten great service
Completed Post insult inspection everything is working properly and will pass code please see pictures attached we had also left hose and light picked that up as well and put back on new return grill
Performed two system cooling maintenance. The main system that services the west of the home is not cooling properly due to a refrigerant leak at the indoor coil. Equipment not registered, out of warranty. Homeowner elected to get system replacement options instead of replacing the coil only. Money used today can be applied towards system replacement, will also install the start assist for the opposite unit as well if we move forward with replacement. Left estimate sheet with homeowner with financing options for 0%/60months and 6.99%/120months
Performed heat PM. Changed filter ,,checked blower motor and inducer, cleaned flame sensor and observed in heat mode to verify everything is venting and working properly and checked for co2 leaks .
Completed diagnosis, found system low on 410A not cooling. Performed electronic leak search, evaporator coil is leaking refrigerant. Possible part warranty. I explained that to homeowner that we look into it. Celeste please check warranty and give quote on replacement. Goodman evaporator coil M#CHPF4860D6DB S#1608Y23228
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Treated drain lines with vinegar and hot water. Tightened all wire connections. Both systems have a good temperature difference. Checked outdoor units. I had to let the heater run in order to have some heat to remove from the home. When I arrived it was 44Â°. Changed out both capacitors. Both were below recommended specifications. Washed both condenser coilâ€˜s. Systems are operating at manufacture specs at this time. Helen and I discussed the issues of dust infiltration in her home. None of the sheet rock penetrations, Canliteâ€˜s or boots in the ceiling are not sealed. I will get a quote and email it back.
Second opinion for client. Long time client at another address, first time here. Inspected both furnaces and found no issues with either system. One system is a zone system. Meaning more than one thermostat on one heater. Blower wheel is slightly dusted. System has utilized a 4 inch filter from the beginning. No carbon monoxide or gas leaks were detected while in attic. Both systems have adequate returns. The 80,000 BTU furnace has an 18 inch duct. Which will carry 1000 CFM. The other system has 1200 CFM. No additional ductwork is necessary as stated on clients previous contractor Milestones. Only recommendation I have today is a Reme Halo. $995.00
Customer cancelled service call.