Heating And Air Conditioning McKinney TX
For over 25 years, AC Pros has brought our customers fantastic professional home comfort. We’re happy to serve your home’s heating and cooling needs in McKinney, TX.
Check out our reviews from customers in McKinney, TX. See why they enjoyed our help with their comfort solutions!
for McKinney, TX
Our Reviews by City
Brent - McKinney, TX
Jason was very passionate and knowledgeable
Great service and spring tune up
Joe - McKinney, TX
Debra - McKinney, TX
The best. Thats why we always ask for him.
Monika - McKinney, TX
We prefer Joel, because we know he will be honest with us. He has been serving our Airconitioner for at least 18 years.
Good service. Helpful and informative.
Justin - McKinney, TX
Really good service. Well done
Jennie - McKinney, TX
Through check of the system. Informed me of the results and expectations of the system.
Great service call for check up
Joe - McKinney, TX
Joel S. is an awesome technician. Just bought our house so I wanted everything checked out and tuned up. As usual, AC Pros did a great job. Always happy with their work.
Gktorranceaolcom - McKinney, TX
Carolyn - McKinney, TX
Arrived to find system not starting due to bad capacitor and turbo was Installed. Turbo capacitor and 3 lbs of refrigerant were added and customer will call about maintenance.
Ac checkup on unit. Inside unit checked along with blower and coil. Condenser checked, air speed checked, fllter checked. Condenser was rinsed and freon was balanced. Compressor Amps, contactor and capacitor all.with range at this time. Suggestions are to fix the drain lines which I'll an estimate for in the invoice. Also to add dampers
2 system Maintenance on trane units. Both condensers checked along with compressor Amps, fan amps, capacitors and hard starts. Capacitor on upstairs was low and replaced with turbo cap. Airflow was also adjusted and turned down on both units. Both condensers were rinsed and pressures for units its will be attached to invoice. BothÂ furnaces were checked, filters checked, blowers checked and the only issue found was with the drain lines. I highly recommend fixing the drains since upstairs system is lacking flood prevention to shut off unit if it does back up.Â Drains cover replacement and come with am ez trap. Can confirm ac is running at this time on all units.Â
AC performance tune up times one system. Filter clean at this time. Inspect blower, evaporator and ductwork. Test thermostat for proper operation. Check outdoor unit. Refrigerant level is okay at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacturer specs at this time.
Heat checkup /ac checkup on heat pump. Pics of pressures will be attached and system components working at this time. Can confirm heat and ac are running at this time.
Ac checkup on 3 trane systems. Pressures for all 3 attached as pics. 2 appear to be low but tends are the 60s and its raining. Recommendations are for hard start kits on all the units and for a drain line upgrade on one of the 3 in the attic. Can confirm ac is running at this time.
2 system checkup on trane units. All system components operating correctly at this time. Onky recommendationse Filters
Heat performance tune up times one system. Inspect blower, evaporator and ductwork. Tested all safety features High limits and roll out. Check heat exchangers for cracks found none. No carbon monoxide or gas leak detected in home. Tightened all wire connections. Test thermostat for proper operations. System operating at manufacturer specs at this time.
Heat check up on 2 units we installed. Both systems are operating at manufacturer specs at this time. Both filter were changed out. House has sidewall registers in the ceilings which are causing some hot and cold spots and reguster replacement was suggested. Some ductwork modifications were also suggested but only if the customer has an issue with current airflow. Can confirm heat is running atthis time. 824 was swapped out under the 10 years P&L warranty.
Heating Maintenance on 3 systems. Checked the heat exchangers. Cleaned the flame sensors and checked the igniters. Checked all the safety switches. Checked the gas pressures and checked for carbon monoxide. There is no carbon monoxide present at this time. Tightened all the electrical connections. Inspected the blower motors and the inducer motors. Inspected the ductwork. Replaced the 20x25x4 filters on all 3 units. The systems are working properly on heat mode at this moment. Outdoor Temperature: 63 DOWNSTAIRS Blower Motor Amps: 8.55 Inducer Motor Amps: .76 Gas Pressure: good Igniter: 55 ohms ( good ) Flame Sensor: clean Pressure Switches: good Heat Exchangers: good Vent Pipe: good Carbon Monoxide: 0 ppm Filter: 20x25x4 Replaced today MASTER BEDROOM Blower Motor Amps: 7.21 Inducer Motor Amps: .76 Gas Pressure: good Igniter: 51 ohms ( good ) Flame Sensor: clean Pressure Switches: good Heat Exchangers: good Vent Pipe: good Carbon Monoxide: 0 ppm Filter: 20x25x4 Replaced today UPSTAIRS B
Heating performance tune up times two systems. Filters good at this time. Inspect blowers, evaporators and ductwork. Test all safety features High limits and roll outs. Inspect heat exchanger for cracks found none. Check for gas leaks found none. Cast thermostat for proper operation. Hooked up second stage 4 downstairs heater, it was never hooked up before. Systems operating at manufacturer specs at this time.
Heat performance tune up times one system. Inspect blower, evaporator and ductwork. Clean flame sensor and inducer port. Check heat exchanger for cracks, found none. Check for gas leaks found none. Tightened all wire connections. System has a 42 degree temperature rise. Filter was changed recently. System is operating at MFG specs at this time.
Made corrections for disconnect, ductwork strapping, and sealing for inspection report as customer is selling home.
System operating at manufacturer specs at this time
Inspection on AC unit. Client is putting the home on the market. Verified drains are sloped properly and draining properly. Inspect it all the ductwork. Verified all caps are sealed with mastic. Tested thermostats on the zone system for proper operation. Check outdoor unit. Refrigerant level good at this time. System is running an 8 degrees subcool. Work condenser coil and return air Grille. System is operating at manufacturer specs at this time.
Capacitor is weak and I would recommend replacing. Compressor is loud and system is only 5 years old. Would also recommend adding a return to system since there is only one. 12" return with 14x14 grille $595
Cleared a simple, clogged main condensate drain, for the master bath&bedroom. Drain terminated at master bath lavatory.
AC maintenance on train system in Allen
Cleaning and maintaining Trane and Carrier air conditioners in McKinney
Providing an estimate on unit replacement in McKinney
Repairing Trane air conditioners in Dallas
Cleaning and maintaining Rheem air conditioners in McKinney
Cleaning and maintaining Trane air conditioners in Allen
Cleaning and maintaining Trane air conditioners in McKinney
Replacing a grill on a Goodman condenser in McKinney