Heating And Air Conditioning McKinney TX
For over 25 years, AC Pros has brought our customers fantastic professional home comfort. We’re happy to serve your home’s heating and cooling needs in McKinney, TX.
Check out our reviews from customers in McKinney, TX. See why they enjoyed our help with their comfort solutions!
for McKinney, TX
Our Reviews by City
Min - McKinney, TX
I got the first time AC Pro free service at the Home and Garden show. The service is easy to schedule. The Technician Justin came in on time and went straight to work. He is friendly and taught me what I need to beware of for the outside AC unit, helped me replace my old air filter, and checked if everything is working properly. Our AC unit is 3 years old. Everything is working well. There’s no hard sell or catch at the end of the service. I am very satisfied with AC Pro.
Brandon - McKinney, TX
AC Pros arrived within a few hours and resolved the AC issue quickly. It’s comforting to know I have a reliable and professional company to call in a less than desirable position. Especially in this weather! Jeff did a fantastic job. Thank you!
Greg - McKinney, TX
Mr. Stevens was very courteous and professional. Arrived on time and completed service quickly. I will definitely use them again.
Very knowledgeable, thank you fix the problem.
Jane - McKinney, TX
Carolyn Glover - McKinney, TX
Donna - McKinney, TX
Joel was great and we are very pleased with his service
Debra - McKinney, TX
Friendly and great service.
Talent installation staff.
Jane - McKinney, TX
Jeff was very informative and helped explain the new thermostat functions. He also explained cold and hot spots in my home.
Elizabeth - McKinney, TX
Great staff, super helpful and attentive to all my concerns and questions
Debra - McKinney, TX
I thought he spent too much time on his phone. Made me wonder how much he was concentrating on the job at hand.
Lee - McKinney, TX
Joel was very polite and super quick.
Great response, service and price on a weekend
Donna - McKinney, TX
Service in McKinney within an hour on Saturday no extra charge.
Poor service, broken promises, waste of time
Anonymous - McKinney, TX
Brent - McKinney, TX
Jason was very passionate and knowledgeable
Great service and spring tune up
Joe - McKinney, TX
Debra - McKinney, TX
The best. Thats why we always ask for him.
Monika - McKinney, TX
We prefer Joel, because we know he will be honest with us. He has been serving our Airconitioner for at least 18 years.
Good service. Helpful and informative.
Justin - McKinney, TX
Really good service. Well done
Jennie - McKinney, TX
Through check of the system. Informed me of the results and expectations of the system.
Great service call for check up
Joe - McKinney, TX
Joel S. is an awesome technician. Just bought our house so I wanted everything checked out and tuned up. As usual, AC Pros did a great job. Always happy with their work.
Gktorranceaolcom - McKinney, TX
Carolyn - McKinney, TX
2019 5 ton zone system Goodman. Cleaned coils checked drain line , turned both zones on to verify the board was operating correctly . Showed them where the filter should go (they were having to remove both return grills to put filter instead of just one inside unit . Checks pressures and got split temp of 21. They will discuss getting a membership and call .
AC performance tune up times two systems. Inspect blowers, evaporators and ductwork. Check thermostat for proper operations. Tightened all wire connections. Verified primary drains of clear at this time. Check outdoor units. Refrigerant levels are good at this time. The Run capacitors are slightly below manufacturer specifications. The cost of the Run capacitors are $250.75 a piece. Wash condenser coils. Advised client to start using 4 in. filters.
Found system to have low charge , found loose Schrader that I tightened and added 1lb 410a. If issue persists then a leak check is recommended.
I spoke with the Customer and explained the situation again. He does not need Refrigerant. He needs more Capacity. I will discuss with Russ tomorrow doing a Whole House Load Calculation for the Customer to confirm the correct capacity needed.
I was Dispatched to a clogged Drain Line. I discussed the issue with and received permission from the Homeowner to install a Drain Line Isolator. I explained how the Drain System works and warned her the Drain sometimes clogs back up when cleared. The Customer asked that Misty contact her for payment.
I was Dispatched to assess a 4 panel mini-split. I found nothing wrong with the System. I believe it is insufficient for the space. I need to talk to Kevin and get him out there to bid a split System ASAP. He is considering cutting his losses and installing a new System and leaving the Mini-Split in place.
Completed diagnostic, found compressor not energizing. Installed Turbo 80/10 microfared and checked charge, everything is working Properly.
Completed service diagnostic, fan motor was spinning backwards because of faulty run capacitor. Replaced part checked charge working properly.
Performed 1 system maintenance inspection, washed down condenser coils, flushed drain lines, blower motor/fan and compressor amperage were good. Refrigerant levels, ductwork and all electrical components is good.
Completed check on system, drop furnace down to 4 ton which matches the outdoor condenser. Also removed dirty filter, we need to schedule to come back and finish charging system properly. Right now my sub cooling is off affecting humidity. Reschedule for Tuesday morning Jeff only. Added 1.5 410a refrigerant has now 10degree subcooling. Humidity level 47%, 22degree differential. Everything is working great at this time.
I was Dispatched to a Home with Humidity issues. I found the System to be operating as intended. I lowered the Blower CFM from 400 CFM TO 370 CFM per ton. This will allow for more moisture removal. I informed the Customer the Local the Heat and Humidity are currently above the operating capacity of most Residential Systems.
Up on arrival found system in hard lockout. Displaying error code 177.04, causing hi head pressure from dirty condenser coils. Washed condenser coils, everything is working fine at this time. Also recommended General maintenance on both systems .
Upstairs no cool. Found system low on refrigerant. Performed leak search and found slab coil to be leaking. Office will check availability and order and call to schedule date to change it out.
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Joe is aware that the filters need to be changed. Verify primary drains are clear at this time. Check thermostats for proper operations. I checked outdoor units. Upstairs system is low on refrigerant.I advise Joe to get ready to purchase a new system soon. Given the age of the system which is 15 years old. At least 2 pounds low of refrigerant
AC performance tuneup times one system. Filter is clean at this time. Inspect blower, evaporator and ductwork. Verified primary drain is clear at this time. Check outdoor unit. Refrigerant level good at this time. Check capacitor and contactor. Washed condenser coil. System operating at manufacture specs at this time.
John h A.
Preform HVAC maintenance on indoor and outdoor units.checked drain line for blockage and mildew , also checked all three amps on motor in range from .6 to 1.0 duct work in attic is good , checked all three outdoor units all three condenser have turbo capacitor 30 for the compressor and 10.5 for the outdoor motor, coils was dirty, so I washed all three coils. contactor are ok , connection are tight. I recommend to add a stop flow to the upstairs unit for bedroom area, pored drain solution for all three units , homeowner changes there own filter
Hey say performance tuneup times one system. Filter needs to be changed and client is aware of it. Inspect blower, evaporator and ductwork. Check thermostat for proper operations. Check outdoor unit. Refrigerant level is good at this time. Check capacitor and contactor. System is cooling properly at this time. I am leaving a quote for a new fresh air ventilation system. One that will give the client the option of turning it on or off.
One time maintenance on the air conditioner. Spec blower, evaporator and ductwork. System is a 2016, 5 ton zoned system. The evaporator coil has oil all over it. Only had a 6Â° temperature difference. Cleared and flushed primary drain line. Checked thermostats for proper operations. The zone system is operating properly. Went outside to check charge. Verified with Sean that the system was extremely low. He stated that the last part of the summer last year and struggled. Check capacitor and contactor. I washed the condenser coil. I am leaving a quote for a new 5 ton box evaporator coil
Perform 1 system AC maintenance washed condenser coil checked refrigerant levels and split. Checked amps on blower. Tested thermostat for proper operations system is cooling properly at this moment
Install new drive on condenser. System came on an operating properly at this time.
No cool. The drive in the outdoor unit is defective. Office will call and check availability March 30.
Performed maintenance on 2 systems: Recommend adding start kit to main unit and contactors to Masterbedroom condenser because contactors are pitted. And main unit over amping on start up. Also Masterbedroom unit is 23 years old beyond life expectancy and could fail at anytime. Recommended adding float drain safety switches to both units to protect ceiling from ceiling damage. Refrigerant levels, drains are clear, run capacitors are in good shape. Systems are functioning at this time. Start kit for main condenser $318.75 Float drain safety switches for two $257.00 Total parts/Labor $575.75
Performed inspection on complete system, gave homeowner education on thermostat, she had a lot of questions on air flow and programming of thermostat. Checked sub cooling, adjust supply dampers. Drain and gas lines are fine. Installers did a great job on installation.
CHANGED OUT COMPLETE SYSTEM AS PROPOSED AND PERFORMED DUCT CLEANING - INSTALLED 2 HOME RUNS - TRANE 10 YR PARTS WARRANTY - DEALER 5 YR LABOR WARRANTY - 5th YR MAINTENANCE ON NEW EQUIPMENT
Completed diagnosis on upstairs system, emergency drain pan is rusted all the way through and primary drain line is clogged up. System is 15 to 20 year old, Recommend replacement Declined right replacement right now. Homeowner will get back with us, need to talk to husband. Replacing drain pan and to clear drain line total $524.10 Gold maintenance membership to cover all three systems $ 533.00. For 1 year.