Heating And Air Conditioning McKinney TX
For over 25 years, AC Pros has brought our customers fantastic professional home comfort. We’re happy to serve your home’s heating and cooling needs in McKinney, TX.
Check out our reviews from customers in McKinney, TX. See why they enjoyed our help with their comfort solutions!
for McKinney, TX
Our Reviews by City
Donna - McKinney, TX
Joel was great and we are very pleased with his service
Debra - McKinney, TX
Friendly and great service.
Talent installation staff.
Jane - McKinney, TX
Jeff was very informative and helped explain the new thermostat functions. He also explained cold and hot spots in my home.
Elizabeth - McKinney, TX
Great staff, super helpful and attentive to all my concerns and questions
Debra - McKinney, TX
I thought he spent too much time on his phone. Made me wonder how much he was concentrating on the job at hand.
Lee - McKinney, TX
Joel was very polite and super quick.
Great response, service and price on a weekend
Donna - McKinney, TX
Service in McKinney within an hour on Saturday no extra charge.
Poor service, broken promises, waste of time
Anonymous - McKinney, TX
Brent - McKinney, TX
Jason was very passionate and knowledgeable
Great service and spring tune up
Joe - McKinney, TX
Debra - McKinney, TX
The best. Thats why we always ask for him.
Monika - McKinney, TX
We prefer Joel, because we know he will be honest with us. He has been serving our Airconitioner for at least 18 years.
Good service. Helpful and informative.
Justin - McKinney, TX
Really good service. Well done
Jennie - McKinney, TX
Through check of the system. Informed me of the results and expectations of the system.
Great service call for check up
Joe - McKinney, TX
Joel S. is an awesome technician. Just bought our house so I wanted everything checked out and tuned up. As usual, AC Pros did a great job. Always happy with their work.
Gktorranceaolcom - McKinney, TX
Carolyn - McKinney, TX
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Joe is aware that the filters need to be changed. Verify primary drains are clear at this time. Check thermostats for proper operations. I checked outdoor units. Upstairs system is low on refrigerant.I advise Joe to get ready to purchase a new system soon. Given the age of the system which is 15 years old. At least 2 pounds low of refrigerant
AC performance tuneup times one system. Filter is clean at this time. Inspect blower, evaporator and ductwork. Verified primary drain is clear at this time. Check outdoor unit. Refrigerant level good at this time. Check capacitor and contactor. Washed condenser coil. System operating at manufacture specs at this time.
John h A.
Preform HVAC maintenance on indoor and outdoor units.checked drain line for blockage and mildew , also checked all three amps on motor in range from .6 to 1.0 duct work in attic is good , checked all three outdoor units all three condenser have turbo capacitor 30 for the compressor and 10.5 for the outdoor motor, coils was dirty, so I washed all three coils. contactor are ok , connection are tight. I recommend to add a stop flow to the upstairs unit for bedroom area, pored drain solution for all three units , homeowner changes there own filter
Hey say performance tuneup times one system. Filter needs to be changed and client is aware of it. Inspect blower, evaporator and ductwork. Check thermostat for proper operations. Check outdoor unit. Refrigerant level is good at this time. Check capacitor and contactor. System is cooling properly at this time. I am leaving a quote for a new fresh air ventilation system. One that will give the client the option of turning it on or off.
One time maintenance on the air conditioner. Spec blower, evaporator and ductwork. System is a 2016, 5 ton zoned system. The evaporator coil has oil all over it. Only had a 6Â° temperature difference. Cleared and flushed primary drain line. Checked thermostats for proper operations. The zone system is operating properly. Went outside to check charge. Verified with Sean that the system was extremely low. He stated that the last part of the summer last year and struggled. Check capacitor and contactor. I washed the condenser coil. I am leaving a quote for a new 5 ton box evaporator coil
Perform 1 system AC maintenance washed condenser coil checked refrigerant levels and split. Checked amps on blower. Tested thermostat for proper operations system is cooling properly at this moment
Install new drive on condenser. System came on an operating properly at this time.
No cool. The drive in the outdoor unit is defective. Office will call and check availability March 30.
Performed maintenance on 2 systems: Recommend adding start kit to main unit and contactors to Masterbedroom condenser because contactors are pitted. And main unit over amping on start up. Also Masterbedroom unit is 23 years old beyond life expectancy and could fail at anytime. Recommended adding float drain safety switches to both units to protect ceiling from ceiling damage. Refrigerant levels, drains are clear, run capacitors are in good shape. Systems are functioning at this time. Start kit for main condenser $318.75 Float drain safety switches for two $257.00 Total parts/Labor $575.75
Performed inspection on complete system, gave homeowner education on thermostat, she had a lot of questions on air flow and programming of thermostat. Checked sub cooling, adjust supply dampers. Drain and gas lines are fine. Installers did a great job on installation.
CHANGED OUT COMPLETE SYSTEM AS PROPOSED AND PERFORMED DUCT CLEANING - INSTALLED 2 HOME RUNS - TRANE 10 YR PARTS WARRANTY - DEALER 5 YR LABOR WARRANTY - 5th YR MAINTENANCE ON NEW EQUIPMENT
Completed diagnosis on upstairs system, emergency drain pan is rusted all the way through and primary drain line is clogged up. System is 15 to 20 year old, Recommend replacement Declined right replacement right now. Homeowner will get back with us, need to talk to husband. Replacing drain pan and to clear drain line total $524.10 Gold maintenance membership to cover all three systems $ 533.00. For 1 year.
Perform 2 system heat pump checked refrigerant levels changed customer supplied filters. Washed condenser coils tested amps on heat strips tested capacitors both systems heating properly at this moment
Heat performance tune up times one system. Inspect blower, evaporator and ductwork. Tested all safety features High limits and roll out. Check heat exchangers for cracks found none. No carbon monoxide or gas leak detected in home. Tightened all wire connections. Test thermostat for proper operations. System operating at manufacturer specs at this time.
Perform 1 system heat maintenance checked all safety components tighten wire connections cleaned flame sensor checked amp draws on blower and inducer. Inspected heat exchanger for cracks found none. Co level 0ppm system is heating properly at this moment
Supply and change out two filters and left two new filters
Performed heat maintenance inspection, talked to homeowner about adding a Reme Halo to system, declined at this time. Furnace is operating properly.
Performed 1 system check out, no gas or carbon monoxide leaks detected. Insulation in attic is sufficient. System is 4years old. No problems found.
Heating performance tuneup times two systems. Joe changes is on filters. Inspect blowers, evaporator and ductwork. Test at all safety features are limits and roll outs. No gas leaks or carbon monoxide detectors in home. Check heat exchangers for cracks found none. Tightened all wire connections. Clean inducer ports and flame sensors. Both units have excellent temperature rise. Check thermostats for proper operations. Replaced Remi halo bulb. UV light and systems are operating at manufacture specs at this time.
Performed heat inspection, Replaced media filters, no gas or carbon monoxide leaks. Heat exchangers flame patterns, limit switches and sensors are operating properly. Recommend adding surge protectors to keep electrical components safe from power surges, and insulation is good.
Perform 1 heat system maintenance checked heat pump mode tested heat strips and checked charge system is heating properly at this moment
Heating performance tuneup times one system. Change out filter client supplied. Inspect blower, evaporator, ductwork and heat exchangers. Found no stress cracks and heat exchangers. No carbon monoxide or gas leaks detected in home. Test all safety features high limits and rollouts. Check thermostat for proper operations. System operating at manufactures bags at this time.
Completed maintenance inspection, recommend surge protectors for insde units. Flame patterns were good, no gas or carbon monoxide leaks. Changed out media filters. Also homeowner purchased surge protectors.
Completed diagnosis, installed Turbo run capacitor, 25/5. Freon was low, declined repairs at this time.
No cool upstairs. Found float switch tripped because the drain was clogged up. Isolated both units with the quick blast we installed and cleared with nitrogen. The drain line itself was clear. There was some buildup in the P-trap. I treated with drain solution and system is flowing properly at this time.