Heating And Air Conditioning McKinney TX
For over 25 years, AC Pros has brought our customers fantastic professional home comfort. We’re happy to serve your home’s heating and cooling needs in McKinney, TX.
Check out our reviews from customers in McKinney, TX. See why they enjoyed our help with their comfort solutions!
for McKinney, TX
Our Reviews by City
Debra - McKinney, TX
I thought he spent too much time on his phone. Made me wonder how much he was concentrating on the job at hand.
Lee - McKinney, TX
Joel was very polite and super quick.
Great response, service and price on a weekend
Donna - McKinney, TX
Service in McKinney within an hour on Saturday no extra charge.
Poor service, broken promises, waste of time
Anonymous - McKinney, TX
Brent - McKinney, TX
Jason was very passionate and knowledgeable
Great service and spring tune up
Joe - McKinney, TX
Debra - McKinney, TX
The best. Thats why we always ask for him.
Monika - McKinney, TX
We prefer Joel, because we know he will be honest with us. He has been serving our Airconitioner for at least 18 years.
Good service. Helpful and informative.
Justin - McKinney, TX
Really good service. Well done
Jennie - McKinney, TX
Through check of the system. Informed me of the results and expectations of the system.
Great service call for check up
Joe - McKinney, TX
Joel S. is an awesome technician. Just bought our house so I wanted everything checked out and tuned up. As usual, AC Pros did a great job. Always happy with their work.
Gktorranceaolcom - McKinney, TX
Carolyn - McKinney, TX
Perform 1 heat system maintenance checked heat pump mode tested heat strips and checked charge system is heating properly at this moment
Heating performance tuneup times one system. Change out filter client supplied. Inspect blower, evaporator, ductwork and heat exchangers. Found no stress cracks and heat exchangers. No carbon monoxide or gas leaks detected in home. Test all safety features high limits and rollouts. Check thermostat for proper operations. System operating at manufactures bags at this time.
Completed maintenance inspection, recommend surge protectors for insde units. Flame patterns were good, no gas or carbon monoxide leaks. Changed out media filters. Also homeowner purchased surge protectors.
Completed diagnosis, installed Turbo run capacitor, 25/5. Freon was low, declined repairs at this time.
No cool upstairs. Found float switch tripped because the drain was clogged up. Isolated both units with the quick blast we installed and cleared with nitrogen. The drain line itself was clear. There was some buildup in the P-trap. I treated with drain solution and system is flowing properly at this time.
Outdoor compressor/fan motor was not working. Installed Turbo run capacitor 45/5. Also customer purchased gold membership, 1st visit in fall.
Completed maintenance check, drains lines are clear, filter is clean, refrigerant levels are in range. Everything seems to be working properly.
Arrived to condenser not coming on found bad capacitor replaced with turbo system came on system cooling at this moment
Arrived to primary drain clogged unclogged it with nitrogen and strap drains advised to have a plumber come check out the 90 degree fitting when pvc drains comes out to see if itâ€™s pitching correctly that could be the culprit system draining properly at this moment
No cool. Condenser not running. Found condenser fan motor defective. Removed and replaced with new universal. System cooling properly at this time
Arrived to primary line clogged installed quick blast and nitrogen clear the line system draining properly
Perform 2 system maintence washed condenser coils changed supplied filters checked refrigerant levels and capacitors both system are cooling properly at this moment
Return today to install another blower motor upstairs. System came on and is operating properly at this time. # no
Completed diagnosis, possible leak in upstairs evaporator coil. Customer will call home warranty for service.
Replace defective blower motor on upstairs unit. Check charge and added1 pound of R 22. System cooling properly at this time.
Completed diagnosis, system was giving me a 126 error code. Repaired corroded wires inside of condenser. Replaced about 4ft of low voltage wire, and reset fault codes. Recommended maintenance agreement, declined at this time.
Performed electronic leak search, found crack in evaporator coil.
left quote for 16 and 18 seer completes 4 ton
AC performance tune up times one system. Inspect blower, evaporator and ductwork. Found inside of furnace cabinet completely covered with sheetrock dust. Recommended to Elizabeth that she is breathing this and it needs to be cleaned. Also cleaned evaporator coil with solution in place. Old blower and pull blower wheel out to clean separately. Check thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. System is operating at manufacturer specs at this time.
Completed a/c maintenance check out, flushed drains,blower/condenser fan amps were good. Compressor amps, found run capacitor below range. Installed Turbo capacitor 70/5. No other problems found. Also talked to customer about surge protectors, declined at this time
Arrived to find system not starting due to bad capacitor and turbo was Installed. Turbo capacitor and 3 lbs of refrigerant were added and customer will call about maintenance.
Ac checkup on unit. Inside unit checked along with blower and coil. Condenser checked, air speed checked, fllter checked. Condenser was rinsed and freon was balanced. Compressor Amps, contactor and capacitor all.with range at this time. Suggestions are to fix the drain lines which I'll an estimate for in the invoice. Also to add dampers
2 system Maintenance on trane units. Both condensers checked along with compressor Amps, fan amps, capacitors and hard starts. Capacitor on upstairs was low and replaced with turbo cap. Airflow was also adjusted and turned down on both units. Both condensers were rinsed and pressures for units its will be attached to invoice. BothÂ furnaces were checked, filters checked, blowers checked and the only issue found was with the drain lines. I highly recommend fixing the drains since upstairs system is lacking flood prevention to shut off unit if it does back up.Â Drains cover replacement and come with am ez trap. Can confirm ac is running at this time on all units.Â
AC performance tune up times one system. Filter clean at this time. Inspect blower, evaporator and ductwork. Test thermostat for proper operation. Check outdoor unit. Refrigerant level is okay at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacturer specs at this time.
Heat checkup /ac checkup on heat pump. Pics of pressures will be attached and system components working at this time. Can confirm heat and ac are running at this time.