Heating And Air Conditioning Hurst TX
When you need expert comfort solutions in Hurst, TX, whether it's HVAC repairs, indoor air quality services and more, AC Pros is the company for you! We're known for our commitment to professionalism and customer satisfaction.
Read our reviews to see why homeowners in Hurst, TX are continuously happy with our team's skilled work.
for Hurst, TX
Our Reviews by City
Tim - Hurst, TX 76054
Checked flame sensors and ignighters, replaced filters and performed co test as well as inspected flu pipe and blower motors
Making texas happier, one customer at a time.
Performed maintenance on 2 systems, no cracks detected or gas leaks found. Heat pump reversing valve, refrigerant levels, run capacitors are good. Everything is operating properly. Also renewed Gold membership for 2 systems.
Perform 2 systme maintenance checked pressures and split heat pump systme checked out good. Gas furnace system is a low on refrigerant conducted a electronic leak search found leak in evaporator coil system is still on warranty with Trane pics of model # and serial number of coil in service titan
Left side system Inducer fan motor- .18 Inducer fan motor capacitor- 3.9 Blower motor amps-1.98 Blower motor capacitor-NA Air proving switches- ok High temp limit switch- Ok Gas valve- operational CO LEVELS- Ok Filter- Changed Igniter ohms- 49 Ductwork- looks good Flame sensor- Ok Flame looks good Tighten all electrical connections Control board- Ok Thermostat- Ok Recommend a surge protection and ATTIC EVALUATION. Right side system Electric heat strips- 19.7 Blower motor-2.01 Contactor-Ok Tightened all electrical connections Controls- Adjusted airflow on each system due to loud registers and velocity of. Fm from the vents.