Heating And Air Conditioning Southlake TX
Our family-owned company is proud to provide heating and cooling services in Southlake, TX and the nearby areas.
Read our reviews and find out why people in Southlake, TX trust our knowledgeable team with all their heat and AC needs.
for Southlake, TX
Our Reviews by City
Marc - Southlake, TX
Jason was terrific
Bob - Southlake, TX
Joel goes out of his way to provide you with the best service possible and to make sure you are completely satisfied. Extremely knowledgeable about every aspect of the operation of the HVAC systems.
Very professional, great service!
Southlake - Southlake, TX
They are very knowledgeable and helpful. They were respectful, quick and on time!
David - Southlake, TX
Professional, knowledgeable, friendly. I’ve used this company for 20 years, never had a bad experience.
Mike - Southlake, TX
Fantastic service! Cole was very professional and knowledgeable. He took the time to explain the problem and presented the options.
David - Southlake, TX
Arrived to find thermostat issue was the problem.
No heat. Upon arrival checked the sequence of operation and system turned on fine. Tested all voltages and amp draws on inducer, blower, board, and gas valve. Everything was within specs. Cycled the system from the thermostat to make sure I was getting proper voltage. Thermostat is sending proper signal. Checked temperature delta between supply and return and it is within manufacturers specs. System heating properly at this time.
3 systems $485.00 per year per system. Quarterly filter change
Both systems working properly in heat mode at this time. Master bedroom system also serves Marcâ€™s office. This system does not have a filter base at the furnace. It uses a 20x25x1 return filter in the hallway by the master and a 1x1x1 in Marcâ€™s office. The return in the hallway is pinched off which reduces the encounter of air returned (picture added). I also noticed that the thermostat for this system is in the hallway between both rooms, which can give in accurate temperatures for the rooms it serves. I would recommend relocating the thermostat into the master bedroom and adding a wireless temp sensor in the office.
Heating performance tune up times two systems. Clean flame sensors, inducer ports and burners. Inspect blowers, evaporators and ductwork. Test all safety features High limits of rollouts. Check heat exchanger for cracks found none. Tightened all wire connections. Test thermostat for proper operations. No gas leaks or carbon monoxide detected at this time. Systems operating at manufacturer specs at this time.
Heating performance tune up times two systems. Inspect blowers, evaporators and ductwork. Tested all safety features High limits and rollouts. Tightened all wire connections. Check heat exchanger for cracks found none no carbon monoxide detected in building. No gas leaks detected in building either. Chamber side need a new secondary drain pan before summer time. It is Rusted severely almost to the point where water will leak through. Did Air Balance for chamber side. Both systems are 20 years old. They are Amana systems. Model #CDB100A. No charge on the maintenance has today. They are complementary via Jim Bradley
Both systems working properly in heat mode at this time. The master bedroom system has a 5â€ filter base. Informed Mr. Bedell that the 4â€ filters wonâ€™t fit.
Heat performance tune up times two systems. Cleaning flame sensors and induce reports. Clean burners on both furnaces. Test all safety features High limits and roll outs. Tighten all wire connections. Change out filter client supplied. Inspect blowers, evaporators and ductwork. Systems operating at manufacturer specs at this time.
Heat performance tune up times five systems. Inspect blowers, evaporators and ductwork. Cleaned all evaporators with solution. And make sure all are draining properly. Had to be extra careful do to units directly above clients getting their hair done. Testing all heat strips. All five Air Handlers have 10kw heat strips. Test it all thermostats for proper operation. Supplied and changed out all 5 20 x 20 x 1 filters. Systems operating at manufacturer specs at this time.
No cool. 5 ton system has a Low pressure cutout. I bypassed and Added 2 lbs of r-410a. Told Mr. Porter if there's another issue well have to do a leak search. He Had his roof replaced last week and said issues didn't arise until then.
Evaluation on 5 Air Handlers that are not draining properly. On a service call before there was A slime buildup in all air handlers. All Air Handlers do not have enough slope towards drains. All units are level long ways as they should be but they should have proper lift to drain away water out of the primary drain pan. Attached to the invoice are videos that I took and pictures. I spoke with Lori, her husband Mitchell and an attorney at the time of this call. I advised them that the original AC contractor should be liable for this. If AC Pros are to make the corrections, it would require three men two full days of Labor. Commercial labor $1200.00 per day for 2 men. So at a minimum the charge would be roughly $2400.00 to correct this problem
Old sensor removed and new one was installed. Can confirm tstat recognized sensor and system was cycle d in and off
Wrong sensor was ordered
Found system coil frozen but with normal high side temps indicating txv issue. Spoke with customer and comfort advisor is set to come out on sat. Customer would like replace and repair options given. Can confirm systems is on but not cooling
No cool on to units. Float switches had turned off the thermostat to stop producing water. Unit above sink area in rear was completely full of water. Had to allow 30 minutes to drain. Over 400 lb of water was in the pan alone. Installed 3 quick blast in order to clear the drains in the future. Systems are draining properly at this time.
Cleaning blower wheels on Trane units in Southlake
Performing a walk thru on a new Trane System in Southlake
Performing a 2 systems heat tune up in Southlake
Doing repairs to the A.C in Southlake
Performing a 2 Systems A.C Maintenance in Southlake
Replacing R22 AC system with Trane 410A system in Southlake