Heating And Air Conditioning Plano TX
The Cooling & Heating Professionals of Plano, TX
When you choose AC Pros for HVAC service, you can trust we will get your home feeling comfortable and cool in no time! Our goal as a business is to provide you with unparalleled customer service, from the smallest fix to the most complex installation. Our devotion to customer satisfaction has allowed us to be Plano’s number one HVAC service company.
We value our clients in a number of ways, including:
- We offer 24/7 emergency service with no overtime fees - Things that break rarely happen at a convenient time, which is why we waive overtime fees after hours.
- Our technicians provide exceptional workmanship - Members of our team regularly undergo the latest HVAC educational seminars and safety training, ensuring your service is done properly and safely.
- We provide a hassle-free maintenance contract - We automatically schedule your unit for its annual maintenance, so you are left with one less thing to remember.
- 100% customer satisfaction guarantee - If you are not satisfied, neither are we. We promise to make things right.
Some of the services we offer in the Plano area include:
- HVAC Repair
- HVAC Installation
- Air Condenser Repair & Cleaning
- Window Installation & Replacement
- Duct Cleaning
- Indoor Air Quality Control
- Attic Insulation
We invite you to check out some of our reviews below. For more information or to schedule your HVAC service, call us today at (972) 591-0199.
for Plano, TX
Our Reviews by City
Excellent service csll
Widom - Plano, TX
Very friendly and knowledgeable tech!
He arrived on time did very well with his service and I am very pleased.
Brenda - Plano, TX
As good a service I’ve ever had from you.
Sam - Plano, TX
Annual Winter inspection
Barbara - Plano, TX
We love seeing Joel for our twice a year inspection. He’s so knowledgeable about our system that we know he won’t ‘steer us wrong!’
Sam - Plano, TX
Betty - Plano, TX
I will always ask for Joel Sisk!
Knowledgeable service rep, friendly, courteous, and fast.
Buddy - Plano, TX
Caron - Plano, TX
I am a long-time satisfied customer
Don - Plano, TX
John - Plano, TX
Carrie - Plano, TX
Kerry - Plano, TX
Great job on the wintry precheck. Is honest about status of equipment and doesn’t oversell.
Linda - Plano, TX
Came the day we needed help. Much appreciated!
Gary - Plano, TX
Jeff was very courteous and respectful. Did everything that could possibly be done.
Richard - Plano, TX
Andre - Plano, TX
Francisco is always very professional, he gets right work and is very fast.
Theresa - Plano, TX
Great. Francisco did a great job.
Great service -great attitude l
Lynn - Plano, TX
Love ACPro -best team and reasonable prices
Great service as always.
Pam - Plano, TX
Long-time customer. Always great service!
Vicky - Plano, TX
Bill - Plano, TX
Very competent and helpful
Anne - Plano, TX
Carolina - Plano, TX
Matt - Plano, TX
We had a difficult problem to find that required multiple visits. However, the technician quickly resolved the issue.
Susanna - Plano, TX
Francisco was quick & courteous! He was professional, & we are so thankful to have cold air again in our home. I also really appreciated the text I received with his name & picture telling me who the technician was & that he was on his way.
Arrived to find wire broken on 24v outside cut it and rewrite it condenser came on system cooling properly at this moment
Heat performance tuneup times one system. Change out filter client supplied. Inspected blower, evaporator and ductwork. Tested all safety features hall limits and roll outs. No carbon monoxide or gas leaks detected in home. System operating at manufacture specs at this time.
Heat maintenance on single system, checked for gas and carbon monoxide leaks no detection. Temperature rise is 35, inducer draft motor, flame patterns and limit switches are working properly. Recommended adding surge protectors declined all repairs,. Price total $348.50
Arrived to find water on emergency drain pan blew drain outs and treated it advised maintenance on drain lines they were really dirty clean water off pan system draining properly
Arrived to find bad capacitor warranty out didnâ€™t have the same size in my truck installed a turbo system cooling properly at this moment
Primary drain was clogged and tripping the in-line float switch. Supported drain line better to give it better fall to the drain hub. Decided not to charge customer since we did his maintenance a week ago
Heat performance tuneup x 1 system. Change out filter client supplied. Check all safety features, high limits and rollouts. System operating at mfg specs
perform 3 system heat maintenance checked safety components clean coils on mini split cleaned both had flame sensors and co levels all 3 systems heating properly at this moment
Heat maintenance inspection: Recommended adding Reme Halo to system to clean environment within home, such mold, dust, bacteria, gases and odors. Also Attic insulation needs to be added, Homeowner will consider having problems addressed. Also no gas or carbon monoxide detected, flame pattern, hot surface igniter was in good shape. No other problems found. Price on Reme Halo $995.00 includes installation.
Heat performance tuneup times one system. Client had already changed his filter. Inspect blower, evaporator and ductwork. Checked all safety features hard limits and rollouts. Check heat exchangers for cracks, found none. Clean flame sensor, and do support and ribbon burners. No carbon monoxide or gas leaks detected. Test thermostat for proper operations. System heating at manufacture specs at this time.
Heating maintenance times one system. Change out filter client supplied. Check all safety features high limits and roll outs. Inspect blower, evaporator and ductwork. No gas leaks or carbon monoxide detector then home. Checked heat exchanger for cracks found none. Test thermostat for proper operations. System operating at manufacture specs at this time.
Heat maintenance, everything is properly, no problems found. Celeste forgot to clock out. Got side tracked. Out at 4:30.
Completed maintenance for 3 systems, all filters needs to be Changed they are really dirty. Upstairs electric heaters are working good. Downstairs/ Masterbedroom flame patterns,flame sensors, no gas or carbon monoxide leaks detected. Recommend installing Reme Halo to upstairs Masterbedroom system for $995.00 installed. Also homeowner will renew membership in spring time we just need to call her.
Heating performance tuneup times one system. Cleaned flame sensor and into support. Blew out burner and ribbons. Inspect blower, evaporator and ductwork. Ductwork needs to be cleaned. Check for carbon monoxide found none. No gas leaks detected in home. Checked thermostat for proper operations. System operating at manufacture specs at this time.
Primary drain pan is cracked leaking water into secondary drain pan. Quote per Russ Teager $3,575.00 10yr. part 2 yr. Labor. 2 ton horizontal Trane box evaporator coil, supply plenum, secondary drain pan. Also 4ft of 8 and 6 flex duct, Masterbedroom system. Homeowner will give us a call when ready.
Heat maintenance: return filter was dirty causing error code. Flame pattern, and sensor is in good working order. No gas or carnon monoxide leaks. System is in good working condition.
Heater inspection, flame sensor/ flame pattern/no gas or carbon monoxide leaks, attic insulation is in good Shape as well as filter. Furnace is in good working order.
Perform 2 system heat maintenance on recently installed units checked for gas leaks checked for co tighten connections changed both filters both systems heating poperly
Completed diagnosis, low voltage and high voltage wires were faulty. Repaired wires checked charge everything is working properly at this time.
Perform 2 system heat maintenance tested heat checked co levels checked all safety components system is heating properly
Removed insulation from one register and resecured one register in the kitchen. Verified both filters are clean at this time. No charge today
Heating performance tuneup times two systems. Supply and change out to 20Ã—25 times for filters. Inspect blowers, evaporatorâ€˜s, ductwork and heat exchangers. No issues found with the heat exchangers. No carbon monoxide or gas leaks detected in home. Test all safety features are limits and rule outs. Clean and their support and flame sensors. Both systems have good temperature rise. 41Â° and 44Â°. Check thermostats forProper operations. System is heating properly at this time.
Completed heat maintenance inspection, no gas or carbon monoxide leaks detected. Flame pattern is fine. Recommend adding surge protectors. Everything is working fine.
Thermostat that was existing was malfunctioning. Removed and installed T cont203AS42MA. Programmed accordingly and left user manual with clients. System operating properly at this time.
Heating performance tuneup times one system. Inspect blower, evaporator and ductwork. Test all safety features high limits and roll outs. Check heat exchangers for cracks, found none. Adjusted drain line for the air conditioner so that it would drain properly. No carbon monoxide or gas leaks detected in home. System is operating properly at this time.