Heating And Air Conditioning Fort Worth TX
With 24-hour emergency services and a 100% customer satisfaction guarantee, it’s easy to tell that AC Pros has your convenience in mind for heating and cooling in Highland Village, TX.
See our reviews below! You’ll learn why people rely on our friendly, experienced team to solve their home comfort issues in Highland Village, TX.
for Fort Worth, TX
Our Reviews by City
Kimm - Fort Worth, TX 76182
Highly recommend! From day one great customer service and communication . Service technicians did a very thorough professional job. Helpful , kind group of professionals!
One system cooling tune up. Inspected indoor coil and blower motor. Tested system pressure and subcooling. Inspected fan motor, capacitor, and contactor. Recommended installing new disconnect for condenser Recommended blower wheel pull and clean or replace blower wheel Recommended new fan motor for condenser Recommended charging system with 410A to the proper subcooling of 13 See estimate
Returned to install evap motor, belly band, turbomini capacitor and blower wheel. System heating properly.
completed install form
Found the control board to be bad. Customer will replace it himself. Due to the style of system the unit should all be replaced at one time to avoid further issues. Left pricing for new units customer will return a call back if they want to move forward.
Heat performance tuneup times one system. Found no issues with heat pump at this time.
2 1/2 ton Trane Full Gas system
Zac Preformed inspection of building 18 units. was not told which unit but just building 17. I assumed that it was the heavily damaged unit. it is running but does look a bit low on refrigerant. there is no electrical cabinet door the motor is leaking oil. wires are too small for unit size. only option with us is to replace the outdoor units as there are numerous code violations for every system. the only storm damage looks to be that one unit.
AC performance tuneup times one system. Client changes his own filter. Inspect blower, evaporator and ductwork. Primary drain is clear and flowing at this time. Check thermostat for proper operations. Check outdoor unit. Refrigerant level is perfect at this time. Checked passer in contactor. System is cooling properly at this time.
Customer currently has a 2 zone system (tstat upstairs and one Downstairs ) it's a 5 ton upflow heatpump with a closet door opening of 30" . The current honeywell zone board is working fine and can be kept . Also the 46x32 slab is in good condition . Condenser is on right side of house with no gate or fence (easy access) air handler is up the stairs in first door. I also filled at a pre I stall form
Heat performance tuneup times one system. Filter was good. Inspect blower, evaporator and ductwork. Test amp draw on 10 KW heat strips. Check outdoor unit. Refrigerant level good at this time. Test capacitor and check contactor. Test defrost cycle. System is heating properly at this time.
no entry to home and no one answered when calling
AC performance tuneup times one system. Filter was good drains are clear. Inspect blower, evaporator and ductwork. Tightened all wire connections. Check outdoor unit. Refrigerant and run capacitor are good at this time. Washed condenser coil. System operating at manufacture specs at this time.
Changed out 2 damaged condenser lids. If you need these tops Dustin let me know if not I will throw them away sir.
Heat performance tuneup x 1 system. Filter good. Check amp draw on 5kw heat strip. 20.5 amps. Refrigerant level good. Contactor and run caps to. System operating at mfg specs at this time.
Breaker is needed to make complete repair on the electric air handler. We could not get the breaker without the total heat package which is $563. I made temporary repair and Russ is giving quote for a new system.
Hey see performance tuneup times one system. Inspect blower, evaporator and ductwork. Check temperature difference in amp draw. Checked thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacture specs at this time.
Installed ECM blower motor, checked everything is working properly.
Completed diagnostic, ecm blower motor is bad. Customer will call us tomorrow, because he may have another company coming out. Also need to call with a price. M#FEM4P3600AT1. S# A122469592
Heating performance tune up times one system. It was suspect blower, evaporator and ductwork. Tightened all wire connections. Tested heat rise .System is a heat pump. Heat rise is 40Â°. Test amp draw on heat strips. 21 amps. Check outdoor unit. Refrigerant level good at this time. Tested defrost cycle. Coil is clean test the thermostat for proper operation. System operating at manufacturer specs at this time.